|Place of Origin:||UK|
|Minimum Order Quantity:||5 Pcs|
|Price:||according to the purchase quantity|
|Delivery Time:||in stock|
|Payment Terms:||T/T payment|
|Supply Ability:||500 pcs|
The MTL5314 connects to a 2- or 3-wire 4/20mA transmitter or current source located in the hazardous area. It supplies one or two configurable alarm signals to the safe area via changeover relays. Each relay may be configured individually to signal an alarm condition (relay de-energised) when the input signal is greater than or less than a pre-set value. In addition, the MTL5314 can be connected in series to the hazardous-area side of an MTL5541 4/20mA repeater power supply (or equivalent device) to provide two trip alarm outputs direct from the transmitter signal (see schematic diagram). Looping the transmitter signal through the MTL5314 (via terminals 1 and 3) does not affect HART® communications.